What are OFNP, OFNR, OFNG and OFCG? Understanding Fiber Optic Cable Fire Ratings
Just like copper cables, NEC (National Electrical Code) requires indoor fiber optic
cables be marked with their fire and smoking ratings. NEC requires all indoor fiber cables
be marked correctly and installed properly for its intended use.
According to NEC, a building's inside area is divided into three types of sections:
plenums, risers and general purpose areas.
What is a Plenum area?
A Plenum area is a building space used for air flow or air distribution system. In most
buildings, the area above a drop ceiling or under a raised floor is used as the air return
(source of air) for the air conditioning. Those drop ceiling and raised floors are also
where fiber cables are often installed. If those cables were burning, they would give off
toxic fumes and the fumes would be fed to the rest of the building by the air conditioner.
As a result, people could be injured even though they are a long way from the fire.
What is a Riser area?
A Riser area is a floor opening, shaft or duct that runs vertically through one or more floors
What is General Purpose area?
All other area that is not plenum or riser and on the same floor is a general purpose area.
Fiber Optic Cable Fire and Smoking Rating Markings
OFNP stands for Optical Fiber Nonconductive Plenum. OFNP cables have fire-resistance
and low smoke production characteristics. They can be installed in ducts, plenums and
other spaces used for building airflow. This is the highest fire rating fiber cable and no
other cable types can be used as substitutes.
OFCP stands for Optical Fiber Conductive Plenum. OFCP cables have the same fire and
smoking rating as OFNP cables but they have a conducting armor or central strength member
which is usually steel. OFCP cables must be properly grounded at both ends. As a result,
OFCP cables can not be installed in the same cable tray or conduit as power cables.
OFNR stands for Optical Fiber Nonconductive Riser. OFNR cables are used in Riser areas
which are building vertical shafts or runs from one floor to another floor. OFNR cables
can not be installed in plenum areas since they do not have the required fire and smoking
rating as Plenum rated cables. OFNP plenum cables can be used as substitutes for OFNR cables.
OFCR stands for Optical Fiber Conductive Riser. OFCR cables have the same fire rating
characteristics as OFNR cables but they have conducting armor or central strength member
which is usually steel. OFCR cables should also be properly grounded at both ends. OFCP
cables can be used as substitutes for OFCR cables. OFCR cables can not be installed in the
same cable trays or conduits as power cables.
OFNG stands for Optical Fiber Nonconductive General-Purpose. They are typically used in
horizontal cabling, single floor applications. OFNG cables can not be used in plenums or
risers. OFNP and OFNR cables both can be used as substitutes for OFNG cables.
OFCG stands for Optical Fiber Conductive General-Purpose. They have the same fire
characteristics as OFNG cables but they have conducting armor or central strength members
which is typically steel. OFCG cables should be properly grounded at both ends. They
should not be installed in the same cable tray or conduits as power cables.
Colin Yao is an expert on fiber optic technologies and products. To learn even more about
duplex fiber optic cable or
simplex fiber optic cable
visit Fiber Optics For Sale Co. web site.
More Networking Topologies Articles:
• A Guide to Broadband Internet Connections
• The Difference Between a Broadcast Domain and a Collision Domain
• The IEEE 802.3 Ethernet Standards
• ISP Multihoming Explained
• System Area Network Interface Cards
• Six Things You Must Know About Fiber Optic Cable Materials
• How Do Fiber Optic Couplers Work and How are They Made?
• Cable: Cat5, Cat5e, Cat6, Cat6A ; What's the Difference?
• LAN Network Protocols - Ethernet, STP, Fiber
• Wireless Network Vlans - How to Implement Wireless Vlans